Final Order Entered: 1. Atmos's deviation from the inspection requirements of 807 KAR 5:006, Section 26(5)(a)1.c. and (5)(c), is approved for its curb boxes and valves designated as Class Two. 2. Atmos shall perform annual accessibility inspections for curb boxes and valves on service lines that are designated as Class One, which includes: a. All curb boxes required to be installed under 807 KAR 5:022, Section 9(17)(a)1. ; b. All curb boxes connected to service lines with indoor meters; c. All curb boxes connected to service lines that serve designated buildings. d. Designated buildings are defined as: i. Any school, hospital, rest or nursing home, shopping center, government building, or recognized day-care center. ii. Any building in a business district. iii. Any building of public assembly that is occupied by 20 or more persons during normal use. Normal use is defined as occupancy on at least five days a week for ten weeks in any 12-month period (days and weeks need not be consecutive). 3. Within 30 days of the issuance of this Order, Atmos shall provide to the Commission information regarding how many of its curb boxes will fall into each class and what the anticipated savings will be under the deviation, as ordered.